It is very important to have Anti-Icing Systems for ground-based gas turbines located in humid climates (where air relative humidity can be more than 80% and dense fog can cause air temperatures to drop below 5 0C). Such climatic conditions lead to ice formation. This ice can plug the inlet filtration system causing a significant drop in pressure in the inlet system, which in turn leads to performance loss. In extreme cases, there is even a possibility that the ice pieces get ingested into the compressor (first blade stage) which may cause foreign object damage. Ice may also cause the disruption of compressor work because of excessive vibration, or surging by decreasing the inlet flow. The major factors that lead to the ice formation in gas turbines are ambient temperature, humidity and droplet size. So, under the climatic conditions which are prone to ice formation, an anti-icing system is employed which heats the inlet air before entering the compressor. Let us discuss some important aspects of Anti-Icing Systems.
The objective of an Anti-Icing System is to prevent or limit the ice formation in the gas turbine inlet path.
Gas Turbine Anti-Icing Systems (GT-AIS) can be categorized in two groups.
- Inlet heating systems
- Component heating systems
Inlet heating systems operate by transferring heat from a heat source (exhaust gases can be used) to the cold ambient air at the entrance of the gas turbine. If the temperature of inlet air raises sufficiently by this heat transfer, icing cannot form in the gas turbine intake.
AxCYCLE™ is a tool, which provides the flexibility and convenience to study various parameters and understand the performance of thermodynamic cycles.