The acronym HRSG (Heat Recovery Steam Generated) is in different sources describing the operation of cogeneration and heating plants, but what does it mean? Heat Recovery Steam Generated (HRSG) technology is a recycling steam generator which uses the heat of exhaust from a gas turbine to generate steam for a steam turbine generating electricity.
The simplest scheme of a Combined Cycle Gas Turbine (CCGT) is presented in Figure 1.
In Figure 1, the exhaust flue gases temperature on the outlet of the turbine is equal to 551.709 ℃. This is a too high a temperature to release the gasses into the environment. The excess heat is able to be disposed of while receiving additional electric power which is approximately equivalent to 30% of the capacity of a gas turbine.
To reach the maximum economical and eco-friendly criteria possible for the installation, many pieces of equipment are used including: a waste heat boiler (HRSG); turbines with a selection for a deaerator (Turbine With Extraction, Deaerator); feed and condensate pumps (PUMP2, PUMP); a condenser (Condenser); and a generator (Generator 2). Exhaust gases entering into the HRSG transfer heat to water which is supplied by the condensate pump from the steam turbine condenser to the deaerator and further by the feed pump to the HRSG. Here boiling of water and overheating of the steam occurs. Moving further, the steam enters the turbine where it performs useful work.