Waste heat boilers are a sophisticated piece of equipment important for recovering heat and in turn protecting the environment. Waste heat boilers are needed during the operation of facilities in the energy sector such as gas turbine plants and diesel engines, as well as in metallurgy and other industries where excessive heat of high temperature up to 1,000 degrees form during the technological processes. Waste heat boilers are used to recover excess heat energy, as well as to increase the overall efficiency of the cycle. Another feature of waste-heat boilers used at these installations is to protect the environment – by disposing of harmful emissions.
This article discusses the accurate modeling of these sophisticated waste heat boilers. We will consider the simulation of a Heat Recovery Steam Generator (HRSG), which is used in a combined steam-gas cycle for utilizing the outgoing heat from a gas turbine plant and generating superheated steam, using the programs thermal-fluid network approach and complexes of optimization.
The HRSG has four main heat exchangers: cast-iron economizer, boiling type steel economizer, evaporator with separator, and superheater.
On the one side of the HRSG, feed water is supplied from the cycle, and on another side, hot gas is supplied from the gas turbine in the process of operation. The water is preheated and goes to the steel economizer where the boiling process begins in the tubes. After the process in the economizers, the water goes to the shell side of the evaporator, where its active boiling occurs. In the separator, the steam-water mixture is divided into saturated steam and overflow. Saturated steam is sent to the superheater, where superheated steam is formed and goes to the steam turbine cylinder. Overflow water returns to the steam formation. An induced-draft fan is used for gas circulation and removal in the HRSG. The HRSG model also has a spray attemperator for steam cooling. The operation principle of desuperheater is the following: feed water is taken from the economizer and goes to the superheater section, passes to superheated steam flow through nozzles, finely divided water droplets mix, heat up and evaporate and as a result, the steam is cooled.