Global warming and the growing demand for energy are two primary problems rising in the power generation industry. A simple solution to these problems has been researched for a number of years. The SCO2 Brayton cycle is often looked into as an alternative working fluid for power generation cycles due to its compactness, high efficiency and small environmental footprint. The usage of SCO2 in nuclear reactors has been studied since the early 2000s in development of Generation IV nuclear reactors, but the idea itself can be traced back to the 1940s. During this time however, no one really looked into the potential of supercritical CO2 since steam was found to be efficient enough, not to mention it was the more understood technology when compared to SCO2. In modern times though, demand of more efficient energy continues to rise and with it, the need for SCO2.
The potential of supercritical CO2 implementation is vast across power generation applications spanning nuclear, geothermal and even fossil fuel. The cycle envisioned is a non-condensing closed loop Brayton cycle with heat addition and rejection inside the expander to indirectly heat up the carbon dioxide working fluid. Read More
Nowadays, gas and steam turbines are contributing to more than 80% of the electricity generated worldwide. If we add the contribution from hydro turbines too, then we reach 98% of total production.
The improvement of the flow path is crucial, and an advanced design can be achieved through several strategies. The aerodynamic optimization of gas and steam turbines can lead to enhanced efficiency. In addition to that, the minimization of secondary losses is possible by introducing advanced endwall shaping and clearance control. Moreover, further increase of efficiency can be achieved by decreasing the losses of kinetic energy at the outlet from the last stage of the turbine. This can be done using longer last-stage blades as well as improving the diffuser recovery and stability.
It is well established that the performance of combustion air turbines (gas turbines) is sensitive to ambient air temperature. As the ambient air temperature increases beyond standard design point (ISASLS), the power output and exhaust gas flow rate reduces while the heat rate and exhaust gas temperature increases. While the trends are similar for heavy duty and aeroderivative gas turbines, due to the inherent nature of design the results are steeper for aeroderivatives. Various types of turbine inlet cooling technologies such as evaporative cooling, refrigerated inlet cooling and thermal energy storage systems have been practiced with varying degree of success, each having its potential advantages and limitations. Simplicity and cost advantage gained in evaporative cooling is offset by limitation of cooling along web bulb depression line (and is a function of site relative humidity). Refrigerated inlet cooling (direct and indirect) offer advantage of higher cooling and lesser sensitivity to site conditions, and result in greater power output with an impact on relative cost and complexity. Selection of optimum technology of turbine air inlet cooling is hence a tradeoff between competing factors.
The complexity of combined cycles, without any turbine inlet air cooling, poses significant challenge in design of steam system and HRSG due to competing factors such as pinch point, heat and mass flows optimization etc. Knowledge of fluid viz properties of standard air (psychrometrics), standard gas for Joule Brayton cycle, steam for bottoming Rankine cycle and refrigerant for cooling system( for refrigerated inlet air cooling) as applied to complete cycle makes the process complete as well as complex. AxCYCLE™ is one such unique tool to simulate such combined cycle processes with multi fluid-multi phase flows including refrigeration. The standard HVAC features can easily be used for inlet air cooling refrigeration and integrated into the CCPP. Once a digital representation of the complex process is replicated and successfully ‘converged’ at design point, the challenge of optimization emerges. To facilitate optimization various tools namely AxCYCLE™ Map, Quest, Plan and Case are embedded integrally. As a first cut, users based on their experience apply AxCYCLE™ Map and vary one or two parameters to see the effect of operational parameters on cycle performance. AxCYCLE™ Quest opens the gates by allowing users to vary unlimited parameters, according to quasi-random Sobol sequences. mutli-Parameter optimization tasks are possible using AxCYCLE™ Plan – it uses design of experiments concepts. Once optimized the AxCYCLE™ Case tools allows off design simulation tasks. Exhibit below represents complexity of a combined cycle plant represented conveniently:
Gas turbines are one of the most widely-used power generating technologies, getting their name by the production of hot gas during fuel combustion, rather than the fuel itself. Today, the industry is clearly driven by the need of fast and demand-oriented power generation, thus additional effort is put in extremely short installation times, low investment costs and an enormously growing volatility in the electrical distribution in order to achieve higher levels of reliability in the power grid .
The majority of land based gas turbines can be assigned in two groups : (1) heavy frame engines and (2) aeroderivative engines. The first ones are characterized by lower pressure ratios that do not exceed 20 and tend to be physically large. By pressure ratio, we define the ratio of the compressor discharge pressure and the inlet air pressure. On the other hand, aeroderivative engines are derived from jet engines, as the name implies, and operate at very high compression ratios that usually exceed 30. In comparison to heavy frame engines, aeroderivative engines tend to be very compact and are useful where smaller power outputs are needed.
Turbine technology being central to energy-producing industry, research and development efforts is directed towards cost-savings (increased efficiency, reliability, and component lifespan), sustainability (alternative fuels, lower emissions), and cost-competitiveness (particularly for the emerging technologies) . This blog post is the first in a series of three that will focus on steam, gas and hydraulic turbines for power generation.
Going back to the Archimides era we will find the idea of using the steam as a way to produce work. However, it was not until the industrial revolution when the first reciprocating engines and turbines developed to take advantage of steam power. Since the first impulse turbine development by Carl Gustaf de Laval in 1883 and the first reaction type turbine by Charles Parsons one year later, the development of turbines have sky-rocketed, leading to a power output increase of more 6 orders of magnitude.
The demands of the plant construction and energy sector after a shorter response time for questions upon newly defined operating points of a turbomachine train are one of the biggest challenges in the service business. This becomes particularly obvious if the future points can only be realized by redesigning the flow-relevant components. Often, it is necessary to have more time to check the dynamic behavior of the train, than in the development of the appropriate revamp measures for the core machine itself.
In addition to the different utilization rates of the affected departments, the causes of the delays often lie in the lack of interface quality between the design/ calculation and train integration team. On top of that, a certain amount of time will be required by manufacturers of the critical components such as gearboxes or drives to perform a lateral check. This lateral check is not only mandatory, in case of a component modification such as changing the transmission ratio or upgrading the drive, but it is also necessary if the coupling between the train components must be changed to ensure torsional stability.
With the blast of the French nuclear power plant a few weeks ago, safety of nuclear power plant designs has fallen under more scrutiny. Although according to sources the blast took place in the turbine hall and no nuclear leak was found, this event has brought more attention to improved design and operation standards.
Following the incident earlier this month Toshiba, a Japanese multinational company, announced the resignation of its chairman following a $6.3 billion loss in their nuclear sector –also withdrawing from the nuclear business. The two back to back events have highlighted the main two problems of nuclear power: high cost and environmental/safety concerns. Said to be a green technology, nuclear power raises concerns with potential nuclear meltdown and risk of safety from toxic waste, accompanying the fact that building a new plant cost around $5,000.00 per kilowatt of capacity with around 6 years of lead time. Each dollar invested on a nuclear power plant has about 2-10 less carbon savings and is 20-40 times slower compared to other alternatives. Yes, evidently nuclear power is found to be very reliable, enabling consistent baseload energy production at any time of day and night. Though, it has been questioned whether this reliability is worth the high cost of nuclear production, in fact all nuclear plants are still operating with 100% subsidized.
Geothermal power market has been showing sustainable growth globally, with many installations in developing countries. As people turn to renewable sources while demand for energy is experiencing rapid growth, geothermal is found to be a reliable energy source and current development is calculated to increase global capacity by over 25%. Geothermal power plants can usually be divided into several types of cycles, including binary, flash, double flash and more. Flash power plants are found to be the most common forms of geothermal power plant and specifically, we are going to talk about the double flash cycle.
A flash system produces high pressure dry steam to move the turbine, generating electricity after going through a flash separator. A double flash system uses two flashes separating systems in order to generate more steam from the geothermal liquid and increase cycle output. The cycle starts with high temperature fluid extracted from a geothermal source to a high pressure separator (HPS) for flashing. The HPS produces a saturated steam that enters the high pressure turbine and the remaining brine is directed into a secondary low pressure separator (LPS). Reducing the flashing pressure increases the mixture quality in the LPS, which results in higher steam production. Low pressure saturated steam is mixed with the steam flow exhausted from the high pressure turbine and the resulting steam flow is directed to the low pressure turbine and produces more electricity. Steam that is exhausted from the low pressure turbine will then be compressed and injected back to the ground. In a flash system, separator pressure has a significant effect on the amount of power generated from the system – and the flashing pressures also influence double flash cycle significantly. In order to optimize one design, the value of parameters versus cost of operations should be taken into account.
Heat recovery steam generators (HRSGs) are used in power generation to recover heat from hot flue gases (500-600 °C), usually originating from a gas turbine or diesel engine. The HRSG consists of the same heat transfer surfaces as other boilers, except for the furnace. Since no fuel is combusted in a HRSG, the HRSG have convention based evaporator surfaces, where water evaporates into steam. A HRSG can have a horizontal or vertical layout, depending on the available space. When designing a HRSG, the following issues should be considered:
The pinch-point of the evaporator and the approach temperature of the economizer
The pressure drop of the flue gas side of the boiler
Optimization of the heating surfaces
The pinch-point (the smallest temperature difference between the two streams in a system of heat exchangers) is found in the evaporator, and is usually 6-10 °C, which can be seen in Figure 2. To maximize the steam power of the boiler, the pinch-point must be chosen as small as possible. The approach temperature is the temperature difference of the input temperature in the evaporator and the output of the economizer. This is often 0-5 °C.
Global warming is a very popular topic at the present time. With the upwards trend of clean technology and the realization that strict climate policy should be implemented, demand of renewable energy has sky-rocketed while conservative plant popularity continues to fall. Additionally, the number of coal power plants have significantly dropped since its peak era, as they are now known as the largest pollutant contribution, producing nitrogen, sulfur oxide and carbon dioxides.
Renewable energy comes from many sources: hydropower, wind power, geothermal energy, bioenergy and many more. The ability to replenish and have no limit on usage and application makes renewable energy implementation attractive. To make this even better, it also produces low emission. Theoretically, with the usage of renewable energy, human-kind should be able to meet their energy needs with minimal environmental damage. With growth rates ranging from 10% to 60% annually, renewable energy is getting cheaper through the technological improvements as well as market competition. In the end, the main goal is to maximize profit while minimizing our carbon footprint. Since the technology is relatively new, capital costs are still considerably higher compared to more traditional (–and naturally harmful) implementations. This begs the question of exactly how we maximize the economic potential of a renewable energy power generation plant.