Often, service companies are faced with the challenge of redesigning existing pumps that have failed in the field with extremely quick turnaround times. While there are quick-fix methods to return these pumps into operation, other more complex problems may require taking a step back and analyzing how this particular pump could be redesigned based on its current operation. These engineering upgrades could solve recurring issues with failure modes of a certain machine, and they could also solve new capacity demands that are imposed by a customer based on their system’s upstream or downstream changes. While efficiency increases could be beneficial to the overall system, many times it is more important to solve capacity requirements and increase the life of the pump by decreasing the Net Positive Suction Head Required (NPSHr).
In this blog post, we will investigate how to move an existing centrifugal pump through the AxSTREAM platform in order to solve engineering challenges seen on common OEM pump upgrades. With the use of AxSTREAM’s integrated platform and reverse engineering module, many of the CAE tasks that are common in an analysis such as this one can be realized in record speed. The first step of the reverse engineering process occurs in obtaining the necessary geometrical information for the desired pump. Through AxSLICE, the user can take an STL, IGES, CURVE file, or a generated cloud of points and properly transform this 3D profile into a workable geometry inside the AxSTREAM platform. In a matter of minutes, the user can outline the hub and shroud and transform a blank 3D profile into a profile defined by a series of segments. Seen in Figure 1, the centrifugal pump is now defined by a hub, shroud, and intermediate section.
In the last post, we covered the area of HVAC dealing with air conditioning and refrigeration. For today’s blog post, we’d like to quickly go over the other major topic of HVAC industry – heating systems. In geographical areas where temperature fluctuation tends to be quite extreme, a good working heating system is a vital necessity –especially during the colder winter months. The main challenge of heating systems frequently comes from the heat distribution method. There are a couple types of heating system and it is important to take into account their functionality to decide which is the best type for your application.
The first systems we are going to focus on is central heating, which is the most common heating system in North American residential applications. This system comes with primary heating applications such as a furnace, boiler, and heat pumps. Each heat source is rather unique and uses different methods of distributing heat into the targeted environment. Furnaces use ducts to blow heated air through in order to disperse the generated energy. Implementation of such technology in the USA is controlled by the Annual Fuel Utilization Efficiency where it estimates seasonal efficiency, averaging peak and part-load situations. Boilers utilizes hot water which travels up to radiators and gets circulated around in a system – so instead of using a fan and ducts, appliances which utilizes boiler as a heat source commonly uses pump to flows the hot water to other parts of the house/building. Since circulation is the most recurring challenge in heating appliances, an optimal pump design must be installed into the system to make sure that the heat is distributed evenly to each part of site. Within central heating there is also heat pump system which works as two-way air conditioner (direct and reverse). During the hotter season, heat pumps work to moving heat from indoor (cooler) to outdoor (higher temperature), and vice versa during the colder months. Heat pumps generally use electricity to move heat from one place to another.
Turbomachinery is a core subject in many engineering curriculums. However, many graduates joining the oil and gas industry are designated as rotating equipment engineers. Though turbomachinery and rotating equipment are used synonymously, all turbomachinery are rotating equipment but not vice versa. Turbinis in Latin implies spin or whirl, and a natural question that arises is – what are the factors that differentiate turbomachinery? In a general sense the term, “rotating” covers the majority equipment used in the industry be it in the upstream, mid-stream or the downstream segment. Yet top rotating equipment specialist in the industry are seen spending their prime time or often being associated with certain unique and specific types of critical rotating machines – the turbomachines.
In a classical sense, turbomachines are devices in which energy is added into or taken out from a continuously ﬂowing ﬂuid by the dynamic action of one or more moving blade rows. By this definition propellers, wind turbines and unshrouded fans are also turbomachines but they require a separate treatment. The subject of ﬂuid mechanics, aerodynamics, thermodynamics and material mechanics of turbomachinery when limited to machines enclosed by a closely ﬁtting casing or shroud through which a measurable quantity of ﬂuid passing in unit time makes the practical linkage to rotating equipment – those which absorb power to increase the ﬂuid pressure or head (fans, compressors and pumps) and those that produce power by expanding ﬂuid to a lower pressure or head (hydraulic, steam and gas turbines). Further classification into axial, radial and mixed type (based on flow contour), and impulse & reaction (based on principle of energy transfer) is common. It is the large range of service requirement that leads to different type of pump (or compressor) and turbine in service.
Operation of most liquid-propellant rocket engines, first introduced by Robert Goddard in 1926- is simple. Initially, a fuel and an oxidizer are pumped into a combustion chamber, where they burn to create hot gases of high pressure and high speed. Next, the gases are further accelerated through a nozzle before leaving the engine. Nowadays, liquid propellant propulsion systems still form the back-bone of the majority of space rockets allowing humanity to expand its presence into space. However, one of the big problems in a liquid-propellant rocket engine is cooling the combustion chamber and nozzle, so the cryogenic liquids are first circulated around the super-heated parts to bring the temperature down.
In Physics, a “Vacuum” is defined as the absence of matter in a control volume. Generally, total vacuum is an ideal extreme condition. Therefore, in reality we experience partial vacuum where ambient pressure is different from zero but much lower than the ambient value.
Depending on the pressure we can have different degrees of vacuum, ranging from low vacuum (at 1×105 to 3×103 Pa) to extremely high vacuum (at pressures <10-10 Pa). For the purpose of comparison, space vacuum might present pressures down to ~10-14 Pa in the interstellar regions.
Vacuum is needed in research and several industrial sectors for a wide range of different applications and purposes. The main way to create vacuum is by first using primary vacuum pumps -machines that relying on the general principles of viscous fluid dynamics.
A major concern for pump system engineers over the last fifty years has been caviation. Cavitation is defined as the formation of vapor bubbles in low pressure regions within a flow. Generally, this phenomenon occurs when the pressure value within the flow-path of the pump becomes lower than the vapor pressure; which is defined as the pressure exerted by a vapor in thermodynamic equilibrium conditions with its liquid at a specified temperature. Normally, this happens when the pressure at the suction of the pump is insufficient, in formulas NPSHa ≤ NPSHr, where the net positive suction head is the difference between the fluid pressure and the vapor pressure at the pump suction and the “a” and “r” stand respectively for the values available in the system and required by the system to avoid cavitation in the pump.
The manifestation of cavitation causes the generation of gas bubbles in zones where the pressure gets below the vapor pressure corresponding to that fluid temperature. When the liquid moves towards the outlet of the pump, the pressure rises and the bubbles implode creating major shock waves and causing vibration and mechanical damage by eroding the metal surfaces. This also causes performance degradation, noise and vibration, which can lead to complete failure. Often a first sign of a problem is vibration, which also has an impact on pump components such as the shaft, bearings and seals.
The use of computational fluid dynamics (CFD) in turbomachinery design is getting more and more popular given the increased computational resources. For the design process, however, there is no need for extensive CFD capabilities as the effort is put on minimizing engineering time while obtaining a design which is about 90% optimized. Here we are presenting two cases where CFD is used to derive significant information for pump design.
First, the influence of the blade shape on the parameters of the single blade hydrodynamic pump was studied by Knížat et al . The investigation of the pump properties was carried out experimentally with a support of CFD methods. The accuracy of applied steady-state calculations was satisfactory for the process of design of a single blade pump, because of the good agreement between measured and calculated power curves.