This post is based on DeLuca’s publication about fatigue phenomena in gas turbines . One of the most significant characteristics of a gas turbine is its durability. Especially for the aerospace industry where engines must meet not only propulsion but also safety requirements, the failure of gas turbine blades is a major concern. The “cyclic” loading of the components associated with generator excursions is one of the principal sources of degradation in turbomachinery. In addition, fatigue can be caused during the manufacturing of the components. There are three commonly recognized forms of fatigue: high cycle fatigue (HCF), low cycle fatigue (LCF) and thermal mechanical fatigue (TMF).The principal distinction between HCF and LCF is the region of the stress strain curve (Figure 1) where the repetitive application of the load (and resultant deformation or strain) is taking place.
HCF is metal fatigue that results from cracking or fracturing generally characterized by the failure of small cracks at stress levels substantially lower than stresses associated with steady loading. HCF occurs as a result from a combination of steady stress, vibratory stress and material imperfections . It is initiated by the formation of a small, often microscopic, crack. HCF is characterized by low amplitude high frequency elastic strains. An example of this would be an aerofoil subjected to repeated bending. One source of this bending occurs as a compressor or turbine blade passes behind a stator vane. When the blade emerges into the gas path it is bent by high velocity gas pressure. Changes in rotor speed change the frequency of blade loading. The excitation will, at some point, match the blade’s resonant frequency which will cause the amplitude of vibration to increase significantly.
An important first step in understanding the gas turbine design process is the knowledge of how individual components act given their particular boundary conditions. However, in order to effectively leverage these individual design processes, a basic knowledge of how these components interact with each other is essential to the overall performance of a gas turbine unit. The power and efficiency outputs of a gas turbine are the result of a complex interaction between different turbomachines and a combustion system. Therefore, performance metrics for a gas turbine are not only based on the respective performances of each turbine, compressor, and combustion system, but also on their interactions. The concept of component matching becomes crucial in understanding how to deal with these systems simultaneously.
In general, gas turbines for industrial applications consist of a compressor, a power turbine, and a gas generator turbine designed into one of two arrangements. The first arrangement invokes the use of the gas generator turbine to drive the air compressor, and a power turbine to load the generator on a separate shaft. This two-shaft arrangement allows the speed of the gas generator turbine to only depend on the load applied to the engine. On a single-shaft arrangement, the system obviously cannot exist at varied speeds and the power turbine coupled with the gas generator turbine would be responsible for driving both the generator and the compressor. A simplified diagram of each arrangement is displayed in Figures 1 and 2.
As time goes by, the demand for energy rises while finite resources gradually diminish. The concept of going ‘green’ or using infinite resources has become more and more common in the marketplace. With this in mind, the abundance and reliability of solar energy makes for an attractive alternative. This is because solar power is different. This statement, of course, begs the question of HOW solar power differs.
Common traditional power plants still utilizes finite fuel. Steam power plants, for example, use the fuel as an energy source to boil water which, in turn, allows the the steam to turn the turbine and drive the generator to produce electricity. Concentrated solar power systems, however, use heat energy from the sun as a heat source – which is renewable. This system works by using utilizing mirrors or mirror-like materials to concentrate energy from the sun and then takes that energy to produce steam. The system can also store the energy that is absorbed during the day, to be used at night when the sun is not present. There are a few different types of concentrated solar power systems which one can choose from.
Heat recovery steam generators (HRSGs) are used in power generation to recover heat from hot flue gases (500-600 °C), usually originating from a gas turbine or diesel engine. The HRSG consists of the same heat transfer surfaces as other boilers, except for the furnace. Since no fuel is combusted in a HRSG, the HRSG have convention based evaporator surfaces, where water evaporates into steam. A HRSG can have a horizontal or vertical layout, depending on the available space. When designing a HRSG, the following issues should be considered:
The pinch-point of the evaporator and the approach temperature of the economizer
The pressure drop of the flue gas side of the boiler
Optimization of the heating surfaces
The pinch-point (the smallest temperature difference between the two streams in a system of heat exchangers) is found in the evaporator, and is usually 6-10 °C, which can be seen in Figure 2. To maximize the steam power of the boiler, the pinch-point must be chosen as small as possible. The approach temperature is the temperature difference of the input temperature in the evaporator and the output of the economizer. This is often 0-5 °C.
The increased use of CFD for turbomachinery design is an outcome of the increasing accuracy thanks to high computational resources. Although the benefits of such computations are strong, the approximations and errors derived from CFD could significantly affect the prediction of crucial parameters such as flow temperature and heat transfer. This article will present the challenges related to uncertainties in turbomachinery CFD, based on “Uncertainty Quantification in Computational Fluid Dynamics and Aircraft Engines” 
The exact definition of boundary conditions presents one of the biggest challenges in CFD and turbomachinery given the high accuracy needed to determine the distributions of the non-uniform conditions to which turbomachinery components are subjected .
Global warming is a very popular topic at the present time. With the upwards trend of clean technology and the realization that strict climate policy should be implemented, demand of renewable energy has sky-rocketed while conservative plant popularity continues to fall. Additionally, the number of coal power plants have significantly dropped since its peak era, as they are now known as the largest pollutant contribution, producing nitrogen, sulfur oxide and carbon dioxides.
Renewable energy comes from many sources: hydropower, wind power, geothermal energy, bioenergy and many more. The ability to replenish and have no limit on usage and application makes renewable energy implementation attractive. To make this even better, it also produces low emission. Theoretically, with the usage of renewable energy, human-kind should be able to meet their energy needs with minimal environmental damage. With growth rates ranging from 10% to 60% annually, renewable energy is getting cheaper through the technological improvements as well as market competition. In the end, the main goal is to maximize profit while minimizing our carbon footprint. Since the technology is relatively new, capital costs are still considerably higher compared to more traditional (–and naturally harmful) implementations. This begs the question of exactly how we maximize the economic potential of a renewable energy power generation plant.
In Physics, a “Vacuum” is defined as the absence of matter in a control volume. Generally, total vacuum is an ideal extreme condition. Therefore, in reality we experience partial vacuum where ambient pressure is different from zero but much lower than the ambient value.
Depending on the pressure we can have different degrees of vacuum, ranging from low vacuum (at 1×105 to 3×103 Pa) to extremely high vacuum (at pressures <10-10 Pa). For the purpose of comparison, space vacuum might present pressures down to ~10-14 Pa in the interstellar regions.
Vacuum is needed in research and several industrial sectors for a wide range of different applications and purposes. The main way to create vacuum is by first using primary vacuum pumps -machines that relying on the general principles of viscous fluid dynamics.
Though fossil fueled power plants aren’t as commonly used anymore, coal fired power generation is still a major source of global electricity, making up about 25% of the market in total. Compared to other options in fossil fuel power generation, coal is found to be the most economical choice as well as a reliable option. Making demands that are heavily reliant on other fuels, such as oil-fired for example, slowly levers to coal power generation. The global reserve of coal can be found in abundance when compared to other energy sources (such as oil for example) as there is about 3 times more of it. Also, IGCC comes with an economic benefit as the price of coal has remained relatively constant, which results in a higher degree of confidence when relying on coal as an energy source in the future.
How Does an IGCC Work?
The system uses a high pressure gasifier to turn coal and other carbon based fuels such as high-sulfur coal, heavy petroleum residues and biomass into pressurized clean coal synthesis gas (also known as syngas). The solid coal is gas-fired to produce syngas by gasifying coal in a closed pressurized reactor with a shortage of oxygen to ensure that coal is broken down by the heat and pressure. Before going out of the system, the syngas runs through a pre-combustion separation process to remove impurities, starting with water-gas-shift reaction to increase concentration of hydrogen and efficiency during combustion process, to a physical separation process (through variable methods). After that, a fairly pure syngas is used as a fuel in a combustion turbine that produces electricity. Waste heat contained in a gas turbine’s exhaust is used to produce steam from feed water that further turns a steam turbine to generate additional electricity.
In the ever-expanding market for waste-heat recovery methods, different approaches have been established in order to combat the latest environmental restrictions while achieving more attractive power plant efficiencies. As gas turbine cycles continue to expand within the energy market, one particular technology has seen a significant upsurge due to a number of its beneficial contributions. Supercritical CO2 (S-CO2) bottoming cycles have allowed low power units to utilize waste heat recovery economically. For many years, the standard for increasing the efficiency level of a GTU (Gas Turbine Unit) was to set up a steam turbine Rankine cycle to recycle the gas turbine exhaust heat. However, the scalability constraints of the steam system restrict its application to only units above 120MW.
Tip leakage is generated inevitably by the clearance between the rotating blades and the stationary casing of a turbine, and is responsible for both the aerodynamic losses in a turbine stage and the high heat-loads in the tip region . To decrease tip leakage and improve component performance, shroud seal structures have been widely applied to modern turbine components, especially to low pressure turbines, because of their advantage on both aerodynamic and structural features. However, due to the complexity of the shroud geometry, the flow structures and thermodynamic process in shroud can be extremely complicated, that is interactions of vortices, separations, jet flow, etc. Thus, because of the complex geometry of shrouds, as well as strong interactions between the tip leakage and main flow, it is not easy to draw a numerical simulation with satisfactory accuracy and time-costing in shrouded turbines. This begs the question of what should the compromise be between using simplified loss models and full 3D CFD analysis for leakage modelling?
In the main flow path of a turbine the flow will always be dominated by the blades shape, while for leakage cases the flow will be dominated by the motion and evolution of small eddies. Rosic et al.  reviewed the importance of shroud leakage modelling in multistage turbines. The comparison of measurements and 3D calculations shows that the flow in shrouded low aspect ratio turbines is dominated by shroud leakage. This is especially true as regards the loss distribution. The rotor shroud leakage flow greatly increases the secondary flow in the downstream stators and drives low energy fluid towards mid-span. It was pointed out that with very low values of shroud leakage the flow is reasonably well modelled by a simple 1D model of the leakage flow, using sources and sinks on the casing. However, for more representative real clearances, full 3D modelling of the seal and cavity flows is necessary in order to obtain reasonable agreement. Given that developing a simulation method with both high precision and fast solving speed is imperatively demanded for engineers to assess new designs, Zhengping Zou et al.  suggested that one of the potential approaches for solving the problem is a method that couples low dimensional models, 1D and 2D models, of the shroud flow with 3D (three-dimensional) simulations of the main flow passage. Specifically, some boundary source and boundary sink is set on the interface between the shroud and the main flow passage, and the source term and sink term are determined by the shroud leakage model. The schematic of this process is given in Fig. 1. The results of his study  demonstrate that the proposed models and methods will contribute to pursue deeper understanding and better design methods of shrouded axial turbines.