Key Symbols

Indexes and Other Signs

Abbreviations

An important objective in the design of a multi-stage axial turbine is to determine the optimal number of stages in the module and the distribution of heat drop between stages.

Typically, a given quantity is the module’s heat drop, and should vary the number of stages and the rotational speed (diameter). It should be understood that the circumferential velocity reduction, and hence the diameters of the stages, reduces the disc friction losses, increase height of the blades (and therefore reduce the proportion of end losses), decrease the flow path leakage. At the

same time it leads to an increase in the optimal number of stages, which causes an increase in losses due to discs friction and an additional amount of the turbine rotor elongation. Immediately aggravated questions of reliability and durability (the critical number of revolutions), materials consumption, increase cost of turbine production and power plant construction.

A special place in the problem of the number of stages optimization is the correct assessment of the flow path shape influence, keeping its meridional disclosure in assessing losses in stages. As you know, the issue is most relevant for the powerful steam turbines LPC. It is therefore advisable for the problem of determining the optimal number of stages to be able to fix the form of the flow path for the LPC and at the same time to determine its optimal shape in the HPC and IPC.

It should also be noted that the choice of the degree of reaction at the stages mean radius (the amount of heat drop also associated with it) must be carried out with a view to ensuring a positive value thereof at the root. Formulated in this section methods and algorithms:

- – May serve as a basis for further improvement of the mathematical model and complexity of the problem with the accumulation of experience, methods and computer programs used in the algorithm to optimize the flow of the axial turbine;
- – Allow the analysis of the influence of various factors on the optimal characteristics of the module, which gives reason for their widespread use in teaching purposes, the calculations for the understanding of the processes taking place in stages, to evaluate the impact of the various losses components on a stage operation;
- – Allow to perform heat drop distribution between stages and to determine the optimal number of stages in a module within the modernization of the turbine, i.e. at fixed rotational speeds (diameters) and a given flow path shape or at the specified law or the axial velocity component change along the cylinder under consideration.

A possible variant of the form setting of n stages group of the flow path can be carried out by taking the known axial and circumferential velocity components in all cross-sections, which the numbering will be carried out as shown in Fig. 3.1.

The axial velocity components we refer to the axial velocity at the entrance to the stages group: Read More