Ground source heat pumps (GSHP) are one of the fastest growing applications of renewable energy in the world, with annual increase of 10% in about 30 countries over the past 15 years. Its main advantage is that it uses normal ground or ground water temperatures to provide heating, cooling and domestic hot water for residential and commercial buildings. GSHP’s are proving to be one of the most reliable and cost-effective heating/cooling systems that are currently available on the market and have the potential of becoming the heating system of choice to many future consumers, because of its capacity for providing a variety of services such as heat generation, hot water, humidity control, and air cooling. Additionally, they have the potential to reduce primary energy consumption, and subsequently provide lower carbon emissions, as well as operate more quietly and have a longer life span than traditional HVAC systems. The costs associated with GSHP systems are gradually decreasing every year due to successive technological improvements, which makes them more appealing to new consumers.
The basic purpose of a GSHP is to transfer heat from the ground (or a body of water) to the inside of a building. The heat pump’s process can be reversed, in which case it will extract heat from the building and release it into the ground. Thus, the ground is the main heat source and sink. During winter, the ground will provide the heat whereas in the summer it will absorb the heat.
A GSHP comes in two basic configurations: ground-coupled (closed-loop) and groundwater (open loop) systems, which are installed horizontally and vertically, or in wells and lakes. The type chosen depends upon various factors such as the soil and rock type at the installation, the heating and cooling load required, the land available as well as the availability of a water well, or the feasibility of creating one. Figure 1 shows the diagrams of these systems.In the ground-coupled system (Figure 1a), a closed loop of pipe, placed either horizontally (1 to 2 m deep) or vertically (50 to 100 m deep), is placed in the ground and a water-antifreeze solution is circulated through the plastic pipes to either collect heat from the ground in the winter or reject heat to the ground in the summer. The open loop system (Figure 1b), runs groundwater or lake water directly in the heat exchanger and then discharges it into another well, stream, lake, or on the ground depending upon local laws. Between the two, ground-coupled (closed loop) GSHP’s are more popular because they are very adaptable.