Update – February 28, 2023: AxCYCLE and AxSTREAM NET are our legacy software packages depreciated by AxSTREAM System Simulation. System Simulation was born out of the union of the legacy AxCYCLE and AxSTREAM NET.
Recently scientists and engineers have turned their attention again to carbon dioxide as a working fluid to increase the efficiency of the Brayton cycle. But why has this become such a focus all of a sudden?
The first reason is the economical benefit. The higher the efficiency of the cycle is, the less fuel must be burned to obtain the same power generation. Additionally, the smaller the amount of fuel burned, the fewer emission. Therefore, the increase in efficiency also positively affects the environmental situation. Also, by lowering the temperature of the discharged gases, it is possible to install additional equipment to clean exhaust gases further reducing pollution.
So how does all of this come together? Figure 1 demonstrates a Supercritical CO2 power cycle with heating by flue gases modeled in AxCYCLE™. This installation is designed to utilize waste heat after some kind of technological process. The thermal potential of the exhaust gases is quite high (temperature 800° C). Therefore, at the exit from the technological installation, a Supercritical CO2 cycle was added to generate electrical energy. It should be noted: if the thermal potential of waste gases is much lower, HRSG can be used. More information on HRSG here: https://blog.softinway.com/en/introduction-to-heat-recovery-steam-generated-hrsg-technology/
Any cycle of a power turbine installation should consist of at least 4 elements : 2 elements for changing the pressure of the working fluid (turbine and compressor) and 2 elements for changing the temperature of the body (heater and cooler). The cycle demonstrated in Figure 1 has an additional regenerator, which makes it possible to use a part of the heat of the stream after the turbine (which should be removed in the cooler) to heat the stream after the compressor. Thus, part of the heat is returned to the cycle. This increases the efficiency of the cycle, but it requires the introduction of an additional heat exchanger.
The heat exchangers used in the sCO2 cycle are of three basic types: heaters, recuperators, and coolers. Typical closed Brayton cycles using sCO2 as the working fluid require a high degree of heat recuperation.
Having examined this scheme and examined the process in detail, we can draw the following conclusions about the advantages of this cycle which is demonstrated in Figure 2: Read More